Fan performance curve
IF THE FAN INLET TEM. IS CHANGED FROM 370 TO 230 DEG.
WHAT CHANGES TO BE MADE IN THE FAN CURVE TO CHECK THE PRESENT OPERATING CONDITIONS?
SHOULD I MAKE A CORRECTION FOR VOLUME IN FAN CURVE
ONLY DENSITY CORRECTION TO BE INCORPORATED IN FAN SHAFT POWER & PRESSURE
CHANGE IN DENSITY WRT TEMP. TO BE INCORPORATED IN ALL THAT IS
I THINK ONLY CORRECTION IN PRESSURE & KW IS REQUIRED & NO CORRECTION IN VOLUME IS REQUIRED FOR CHANGE IN TEMP. TO DRAW A NEW FAN CURVE WITH NEW TEMP.
Know the answer to this question? Join the community and register for a free guest account to post a reply.
Re: Fan performance curve
The simplified relationships to extrapolate a centrifugal fan (or pump) curve are as follow:
Flow2=Flow1 * (Speed2/Speed1)
Pressure2=Pressure1 * (Speed2/Speed1)^2 * (Density2/Density1)
Power2=Power1 * (Speed2/Speed1)^3 * (Density2/Density1)
Flow is the fluid volume per unit of time in actual conditions (for example in actual cubic meters per hour and NOT in Normal cubic meters nor in kg/hour)
Pressure is the pressure increase (head) produced by the machine
Speed is the rotational speed of the machine
Density is the density of the fluid (which for a gas is of course heavily depending on the temperature)
These relationships are simplified because they consider that efficiency of the machine is constant.