Raw Mill main drive
We change the NDE bearing of raw mill main drive (3.3 MW) , with decouple condition it was taking 74-76 Amps while coupled with Raw mill (No load) it was taking 27 Amp. This low amps are not digestible to me. Any body help me to avaluate this low Amps.
Know the answer to this question? Join the community and register for a free guest account to post a reply.